EuroSun2008-5

# Selection of the best fitting surface

To be able to calculate the thermal performance of one specific thermosiphon DHW system, it is necessary to identify the surface that describes the thermal behaviour of the system in the best way. For the selection of the best fitting surface, the result of at least one DST test per product line is needed. In Table 2, an example for a product line of six different DHW systems is given. The solar fractions of system 1, 2 and 6 have been determined based on measurements according to the DST method and on a long term performance prediction. The solar fractions of system 3, 4 and 5 are not known a priori and have to be calculated by the extrapolation procedure. The best fitting surfaces is defined as the surface where the discrepancies between the values offsol obtained by the DST method and obtained with equation (2) are minimum. These values are compared with the fSol-values that have been derived directly for the DST measurements. The differences Afsol, between measured and predicted values is calculated with equation (3),

sol, i, j sol, measured sol, calc, i, j

with i = 1...3: system number, j = 1....12: surface number.

The total difference AFsol is defined as the summation over the differences Afsoi? i

AF, o =Z|A«,u

i

Table 2. Example for one typical product line

 System no. Collector aperture area [m2] Storage tank volume [m3] fsol [-] 1 2.0 0.3 0.572 2 4.0 0.3 0.725 3 6.0 0.3 ? 4 2.0 0.5 ? 5 4.0 0.5 ? 6 6.0 0.5 0.830

It is assumed that the surface where the value of AFsol is minimal describes the system behaviour in the best way. This function will then be used to compute the solar fraction for the remaining systems 3, 4 and 5. Table 3 lists the results determined by the mathematical extrapolation procedure according to equation (3) for the solar fractions of systems 3, 4 and 5.

Table 3. Results determined by the extrapolation procedure for system 3, 4 and 5

 System no. Collector aperture Storage tank fsol [-] area [m2] volume [m3]

1st International Congress on Heating, Cooling, and Buildings^ 7th to 10th October, Lisbon - Portugal /

 1 2 0.3 0.572 2 4 0.3 0.725 3 6 0.3 0.828 4 2 0.5 0.549 5 4 0.5 0.723 6 6 0.5 0.830

## EuroSun2008-5

### Automatic Control System

The whole automation system is mainly divided into two parts: one part is the hardware equipments consisted of all kinds of devices used in the testing system; the other part …

### The application of the regulations minimal solar collector area

Following the new regulations, a three bedrooms autonomous zone must have a minimal collector area of 4 m2 independently of the climate zone were is located. From the simulations results …

### Measured sequences used for validation purposes

The comparison of experimental and calculated instantaneous power results, obtained after the different approaches presented in the previous section, is based on instantaneous efficiency measurements for a CPC collector (C …

## Как с нами связаться:

Украина:
г.Александрия
тел./факс +38 05235  77193 Бухгалтерия
+38 050 512 11 94 — гл. инженер-менеджер (продажи всего оборудования)

+38 050 457 13 30 — Рашид - продажи новинок
e-mail: msd@msd.com.ua
Схема проезда к производственному офису:
Схема проезда к МСД

Партнеры МСД

## Контакты для заказов шлакоблочного оборудования:

+38 096 992 9559 Инна (вайбер, вацап, телеграм)
Эл. почта: inna@msd.com.ua